What can we help you with?
Is there a -50° C option for 4800 load bank?
Yes, a load bank option for when -50° C operation is required.
- Avtron uses special motors rated for low temperatures. Supplement heaters (800 W typical) are added with heater power expected to be supplied at all times.
- Avtron would replace any airflow switches with current sensors that monitor the blower motor. Sensors are added to monitor the intake overtemperature.
- Special load wiring (for example silicone-based insulation) is rated for low temperature.